A meat packing facility and tannery in the Midwest US, processing 2.5 millions gallons per day (MGD) of wastewater, with a NPDES (National Pollutant Discharge Elimination System) permit for discharge to a river, had been using both hydrated lime and magnesium hydroxide for 10 years to try and control pH in a low rate anaerobic digester.
The Ca(OH)2 in AMALGAM-55 was formulated at a level sufﬁcient for improved microorganism activity, but not enough to cause an increase in “inert” mineral solids.
AMALGAM-55 gave pH control performance at a dose comparable to the use of magnesium hydroxide on its own.
Because AMALGAM-55 is less expensive than magnesium hydroxide, the customer enjoyed a 15% chemical cost reduction, along with improved microorganism performance.
IER’s Pasco Plant, Washington, USA.
A Midwestern meat processing facility and adjacent tannery was generating over 2.5 million gallons per day (MGD) of high strength organic wastewater. The wastewater treatment facility has a National Pollutant Discharge Elimination System (NPDES) permit for discharge to a river.
When a low-rate anaerobic digester was installed about 10 years ago, magnesium hydroxide (60% Mg(OH)2) slurry was selected for pH and alkalinity control based on its strong but gentle buffering ability.
Through the use of magnesium hydroxide, the optimal pH range for aerobic and anaerobic microorganism performance can easily be maintained, with no pH spiking. Because of its gentle buffering nature, it is virtually impossible to overfeed Mg(OH)2 above a pH of 9.
pH spikes from the use of caustic, soda ash, or lime can shock the aerobic and anaerobic populations into periods of very poor BOD (Biological Oxygen Demand) removal. Unlike caustic or soda ash, which add sodium, magnesium hydroxide adds nutrient value (magnesium) into the secondary treatment and anaerobic biological processes.
<- Owned by Calix, IER (International Environmental Resources) is a distributor of magnesium hydroxide products and other innovative environmentally-friendly process water and wastewater treatment chemicals and equipment.
Based in Spokane, Washington, IER primarily services the Paciﬁc Northwest and Upper Midwest.
Though the magnesium hydroxide treatment was working well for pH and alkalinity control, the facility was continually struggling to develop a diverse microorganism population for improving the overall activity of the sludge. Based on consulting advice to add more calcium to the system, they switched to the use of Hydrated Lime (Ca(OH)2).
In wastewater, lime is often used as an alkalinity supplement. But the effects of lime addition can have undesirable side impacts on the biological system, such as scaling and pH spikes.
Another signiﬁcant, yet overlooked impact is the EPA documented sludge production typically associated with lime.
“The addition of treatment chemicals, especially lime, may increase volume of waste sludge up to 50% which can result in exhorting costs related to the disposal of the sludge dewatering and disposal..” EPA – wastewater technology fact sheet.
The application of lime lasted only a couple of months, as they were astounded at the increase in the inert solids loading in the anaerobic system. This was measured as the ratio of Volatile Solids (VS) to Total Solids (TS).
The ratio of Volatile Solids (VS) to Total Solids (TS) in the system was dramatically decreased from operating in the range of 75-85% with Mg(OH)2 to a range of 30-50% with Ca(OH)2.
In an ideal system, the percentage of VS is greater than 90%, meaning that most of the solids in the system are “bug bodies” or other organic matter. The lower the percentage of VS, the higher the percentage of “inert” or mineral solids in the system.
By signiﬁcantly dropping the ratio of Volatile Solids (VS) to Total Solids (TS), lime Ca(OH)2 can increase operational and maintenance costs related to scaling and sludge disposal.
The reduced percentage of VS during the period of lime usage is consistent with the formation of insoluble calcium minerals, such as gypsum (CaSO4) and limestone (CaCO3) from complexation of calcium with the high levels of sulfate (SO4²-) and carbonate (CO3²-) present in the meat processing and tannery wastewater streams.
The added costs resulting from the need to remove waste sludge at a much more rapid rate (increased sludge disposal costs / hauling fees) as well as a dramatic increase in pumping and plugging problems, resulted in the facility switching back to magnesium hydroxide.
With magnesium hydroxide use, the resulting salts of magnesium sulphate (epsom salt, MgSO4) and magnesium carbonate (magnesite) are thousands-fold more soluble than the corresponding calcium salts (gypsum and limestone). Hence these ions remain in solution and do not become a part of the solids fraction, resulting in a much higher VS-to-TS ratio.
Increased inert solids => extra sludge disposal costs*
Sludge is an expensive and problematic byproduct of the wastewater treatment process.
*Sludge disposal costs = pumping + energy use + hauling
Hydrated lime Ca(OH)2 can increase operational and maintenance costs related to formation of scale and accumulated solids/sludge.
IER takes pride in being a technically credible wastewater treatment company, not simply a magnesium hydroxide supplier.
For over 20 years, IER has worked with plant engineers and operators to offer the most cost effective solutions for their speciﬁc needs.
This results driven approach is what allows us to work with plant management to determine a minimum amount of calcium required as a feed supplement into the system. With this information, a proprietary blended product was formulated to contain predominantly magnesium hydroxide, with a minor component of calcium hydroxide. In this case, the Ca(OH)2 was formulated at a level sufﬁcient for improved microorganism metabolism and not in an excess to cause an increase in the “inert” solids as was observed with straight lime feed.
The feed of this blended product, called AMALGAM-55, resulted in improved microorganism activity while not impacting the ratio of Volatile Solids to Total Solids.
The plant has been using AMALGAM-55 for the past 12 years while maintaining the percentage of Volatile Solids in the range of 75-85%, identical to that observed with the use of straight magnesium hydroxide.
In addition, though formulated to contain only 55% total solids, the required dose for AMALGAM-55 to maintain the desired pH and alkalinity was equal to or less than that required for 60% Mg(OH)2.
By combining the lower cost raw material of hydrated lime into the formula, the overall product price for AMALGAM-55 was less per lb than that for straight magnesium hydroxide.
We pride ourselves in being a wastewater treatment partner:
High quality products
Proactive customer service
The results of this study demonstrated that signiﬁcant performance beneﬁts can be observed by formulating alkalinity supplements into blended products to address the needs of the wastewater microorganism population.
AMALGAM-55, an innovative blend of magnesium hydroxide and calcium hydroxide, was found to provide comparable pH and alkalinity control to that of straight 60% magnesium hydroxide, while also providing a nutritional supplement of calcium for improved microorganism diversity and activity.